Please use this identifier to cite or link to this item:
|關鍵字:||商用抑制劑;非商用抑制劑;電廠廠用冷卻水||出版社:||國立中興大學工學院;Airiti Press Inc.||Project:||興大工程學刊, Volume 15, Issue 2, Page(s) 125-132.||摘要:||
In the presence, molybdate is added as corrosion inhibitor to the cooling water system of one power plant. Monitoring the inhibitory efficiency of corrosion inhibitor, it was found that the slime generated from the cooling system was accelerating t he corrosion of the cooling system. In order to avoid the corrosion of the cooling system, the main purpose of this research is to isolate and identify the bacterium strains from the slime. The inhibitory efficiency of antimicrobial agents to these strains was examined, in order to find the appropriate type and dosage of the antimicrobial agent. The result showed that the cooling water contains rod-shaped bacteria and filamentous microorganism. Six strains were isolated from the slime of the cooling water system. Commercial antimicrobial agent P could not inhibit the growth of the six strains and the slime of the cooling water system. Commercial antimicrobial agent P and Noncommercial antimicrobial agents N, H could inhibit the growth of the six strains and the slime of the cooling water system. The inhibitory efficiency sequences were noncommercial antimicrobial agents N, noncommercial antimicrobial agents H and commercial antimicrobial agent P.
|Appears in Collections:||第15卷 第2期|
Show full item record
TAIR Related Article
Items in DSpace are protected by copyright, with all rights reserved, unless otherwise indicated.